Minimum random time-out for sending an alarm to the Scada. It is then possible to read the internal states of the equipment and the events stored in memory g the T see also section on Commissioning. Easergy T P — Schneider Electric Belgique Otherwise, reset the Power supply module to trigger a battery test, after connecting battery to the rack; if the problem recurs after charging for 24 hours, replace the batteries. In 1 ms increments. Otherwise, after reconnecting the battery, reset the Power Supply module to trigger a battery test; if the problem recurs after charging for 24 hours, replace the battery.
|Published (Last):||2 April 2019|
|PDF File Size:||18.22 Mb|
|ePub File Size:||1.73 Mb|
|Price:||Free* [*Free Regsitration Required]|
The advantages of this type of battery include the fact that there is no risk of explosion, no acid leakage and no servicing requirement. Two versions are embedded, which protects downloading and switching. The shields must be earthed at one point in the line preferably on the PC side of the remote control station. MV network remote control system for the Easergy range cont.
Reducing operating costs b The accuracy of fault information significantly reduces the time required to locate faults: There is therefore a specific type of page for: Orders from the remote control centre are validated.
Battery autonomy b Duration: It performs a complete test of the acquisition system. It operates independently using power supplied by the T In addition to the TST functions, it is also used to: To do this, disconnect the battery and measure the voltage on the rack battery connector. Files download — Diagnostic pages 18 A Files download sub-menu allows these logs to be saved to the PC in the form of Excel-compatible files. SW2 current option 3 — pin plug-in connector: Turn the lock button on the left-hand side of the door a quarter of a turn and open the door.
Easergy T P — Schneider Electric Belgique PE Compact enclosure The equipment is housed in a stainless steel enclosure, ensuring: The Power supply module is designed to optimize the characteristics of the battery. Monitoring page Home page This page can be used to consult the T states: The enclosure shall mandatorily be powered from a LV easregy coming from the MV line on which the component is installed.
This port can also be used for direct connection of the T with the PC. It is a 5 x 20 mm, 4 A time-lag fuse. It is important to know these addresses in advance in order to start a connection these addresses are indicated on the Com card: The presentation, quantity of data displayed and content of this page may vary from one application to another. It is available as an option specific software version.
Rapid return on investments b Comprehensive solutions which are quick and easy to implement. These functions require no on-site programming. In either case, the calculation formula function is included as a standard feature see page Various pages and sub-pages can be accessed by the user depending on the rights available to him.
When the maximum number is exceeded, the oldest event on the list is erased by the most recent one. Use of an external fault detector with a fault reset output.
U1 1 U2 2 Reset 3 4 Causes of automation locking: If you have dummy devices, install them on the HA10 connectors to ensure that neither the battery nor the MV cubicle is overloaded. Automatic setup time PC time Date: PEEN Consulting the logs The various logs available events, alarms and system make it possible to know the history of everything that has occurred on the T This information can be transmitted to the control centre and archived in logs for consultation and local downloading in the form of filesby connection of a microcomputer.
Replacing the Power supply module The fuse located on the Power supply card protects the 12 V supply to the entire rack. Installing a Current or Digital Acquisition card Acquisition cards a Power down the enclosure see the previous pageb Remove the Interface card see abovec Place the Acquisition card in position and secure t with two screws, d Replace the Interface card, e Power up the enclosure.
Easegry Available space see illustration opposite b Height: Automatic control can then operate again. Related Posts.
Kazragore Check the charger and the battery. Combining phase and neutral faults rather than indicating them separately Defining a synthesis of internal faults Managing other equipment of the MV substation such as the light control, etc. In the lock button, a lock or a padlock makes it possible to lock enclosure opening completely. It is 2t00 to slide this window when the lock button is in the horizontal position and access the various control panel options. Time-stamped events see Appendix B As a result of the monitoring operations performed by the equipment, time-stamped events that can be used to track the various operating phases operating mode, transmission of orders to the MV switches, self-testing, and so on are stored. It contains all the functions required to monitor and control the motorized cubicles: The time before sending an alarm is defined randomly between the min. The following functions can be incorporated in the formulas: Earthing d The equipment must be earthed to ensure E.
EASERGY T200 PDF
Samum Incoming voltage 1 Operating modes b The operating mode is selected from the Easergy T configurator. It also allows definition eeasergy user access rights by login and password. To replace the fuses: Each class covers a category of information so as to facilitate viewing on screen. It includes connection cables and does not require any modifications to the T wiring. The serial link is provided on the SUB-D 9-pin connector also located on the right-hand side of the rack. A Digital Acquisition card manages one way. Upstream protection should also be equipped with a Voltage Time automation system.